Select region and country
Diesel < 2572 kVA
Gas < 1183 kVA
Diesel < 90 kVA
Diesel < 51 kVA
Diesel < 2536 kVA
Diesel < 2555 kVA
We have detected that you are using Internet Explorer
For a better user experience on our website, we recommend that you access with another browser, such as
| Chrome | Firefox | Edge | Safari |
If you decide to continue browsing with Explorer, we inform you that many functionalities, menus, banners..., will not run correctly.
Hemos detectado que estás usando Internet Explorer
Para una mejor experiencia de uso en nuestra web, te recomentados que accedas con otro navegador, como por ejemplo
Si decides seguir navegando con Explorer, te advertimos que muchas utilidades, menús, etc de este website no funcionarán bien con él.
The power generation industry has adapted to the specific characteristics of these installations with generator sets specifically designed for Data Centres, sized according to the DCP (Data Center Power) power declaration and which comply with the regulations that apply to them. The Uptime Institute is one of the most internationally recognised
organisation that specify and certify how Data Center installations must be designed. Depending on their availability, it classifies them into four levels: Tier I, II, III, IV. The factor that defines whether a facility is in one or another level is precisely the number of available sources of continuous supply and emergency supply and its maintainability.
The more critical data stored in a Data Processing Centre (DPC), the more secure the power supply that feeds it must be. For this reason, HIMOINSA generators for these projects include a redundant starting system: Either electric & pneumatic or double electric plus additional components, which ensures 100% engine starting.
Its response is extremely fast thanks to the engine preheating with pump . The water is kept at a minimum temperature of 40°C and so the generator set is able to start up in ten seconds. The engine for a DCP application must have an electronic speed regulator to be able to quickly reach favourable voltage and frequency conditions when a mains failure demands its start-up and once these parameters are stabilised, to keep them that way while it is running.
The energy consumption of these Data Centres is significant, not only for the ordinary operation of the IT equipment , but also to keep the rooms in which they are located at the right temperature for optimal server performance (20ºC). Therefore, not only the application-specific aspects, but also the on-site conditions such as ambient temperature and altitude are taken into account when sizing the generator set.
By filling in this form you are consented to having your data processed and recorded on our system and for the management of your relationship as a user, client or candidate for employment at Himoinsa China.
Indicate the type of request